Buy Analogue input module,IE8 mA IE8. Browse our Mfr. Part No. IE8; Brand Allen Bradley I/O,module,Flex User Manual. Legislation. (Cat. No. IE8 Series B). 4. 1. 3. 2. 5. 6. 7. Module Installation. This module mounts on a terminal base unit. 1. the module. Installation Instructions. User manual • Read online or download PDF • Rockwell Automation IE4XOE2,IE8,OE4,D FLEX I/O ANALOG MODULE User.
|Published (Last):||14 March 2008|
|PDF File Size:||5.35 Mb|
|ePub File Size:||12.21 Mb|
|Price:||Free* [*Free Regsitration Required]|
This bit is set 1 when an error is detected in slot position 5. This software tool can be connected to the adapter via the DeviceNet network.
Change Bars The areas in this manual which are different from previous editions are marked with change bars as shown to the right of this paragraph to indicate the addition of new or revised information. Underrange bits U for individual channels 4 20mA current input only Bit 00 corresponds to input channel 0, bit 01 corresponds to input channel 1, and so on. This bit is set 1 when an error is detected in slot position 7.
Connecting Wiring for the Analog Modules. At present, these consist of: Refer to range selection above. When you remove or insert a module with field-side 1794-ue8 applied, an electrical arc may occur.
Position the terminal manuak unit up against the adapter and push the female bus connector into the adapter. Press the terminal base down onto the DIN rail until flush. Bits Bits 15 17 Bits Bits 15 17 Definition Channel 0 Safe State analog value – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits.
Refer to the following table for 179-4ie8 terminal base units that you can use for each module. An electrical arc can cause personal injury or property damage by: Thereafter, the program continuously performs read block transfers and write block transfers. If a negative number is given in two’s complement, its complement a positive number is found in the same way: Multiplex control bits M for individual channels. The new node address does not take affect until the adapter has been powered down and then powered back up.
These instructions let the adapter obtain input values and mnual from the module, and let you send output values manyal establish the module’s mode of operation.
Secure to the wall with two 6 self-tapping screws. SLC — use the scaling instruction.
IE8 & OE4 User Manual_百度文库
Bit 00 corresponds to channel 0, bit 01 corresponds to channel 2, and so on. The first word of input data sent by the adapter is the Adapter Status Word. Full range bits F for individual channels – Bit 00 corresponds to output channel 0, bit 01 corresponds to output channel 1, and so on.
Your program should monitor status bits, block transfer read and block transfer write activity. Position the module 4 with its alignment bar 5 aligned with the groove 6 on the terminal base.
Press firmly and evenly to seat the module in the terminal base unit. This bit is set 1 when an error is detected in slot position 2. Channel 3 analog data – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits. The analog modules have selectable ranges as shown 1794-e8 the table below: Engineering and Field Services.
The configuration register can be cleared by either a reset, or by the user writing all zeroes to it. Use the following formula: This bit is set 1 when the node address switch setting has been changed since power up.
Rockwell Automation 1794-IE4XOE2,1794-IE8,1794-OE4,D17946.5.2 FLEX I/O ANALOG MODULE User Manual
This is the block transfer control file. Other Comments Use back for more comments. Configure select bits C for individual channels – Bit 08 corresponds to output channel 0, bit 09 corresponds to output channel 1, and so on. Channel 2 Safe State analog value – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits.
Since there are many variables and requirements associated with any particular installation, Allen-Bradley does not assume responsibility or liability to include intellectual property liability for actual use based upon the examples shown in this publication. PLC 3 Programming Block transfer instructions with the PLC-3 processor use one binary file in a data table section for module location and other related data.
This bit is set to 1 when all bits in the configuration register write word 3 are 0 unconfigured state.
Identifies information that is especially important for successful application and understanding of the product. The 4—20mA mode scales in the module and uses all 16 bits. Marketing Communications, Allen Bradley Co. Underrange bits U for mannual channels 4 20mA current input only – Bit 00 corresponds to input channel 0, bit 01 corresponds to input channel 1, and so on.
The module is configured using a group of data table words that are transferred to the module using a block transfer write instruction.
Compliance to European Union Directives. If the adapter does not establish communication with the module, cycle power to the adapter. Channel 1 Safe State analog value – 12 bit left justified two’s complement number; unused lower bits are zero; 4 20mA uses all 16 bits.
Channel 0 Safe State analog data sign bit. Features of your Analog Modules.